Peter Dinnage of Climalife explains how it’s not just for Supermarkets
With uncertainty over where the proposed changes to the F-Gas regulations may settle, there are a number of reasons to look at alternatives to R404, especially for new equipment. The selection of refrigerant based on GWP can be a reason, as R404A has a value of 3922, whilst the GWP of Performax LT (R407F) is more than half at 1824.
However, energy efficiency and carbon footprint reductions are other important considerations.
The following three examples of industrial applications all choosing to use Performax LT instead of R404A in new equipment are the first of many as others follow in 2013.
The storage room in question contained a floor-standing cooler with a conventional thermostatic expansion valve, fixed speed compressor and fixed speed condenser fans operating with pressure switches set for year-round operation. JD Cooling began the project by creating a new and bespoke design for the equipment, still incorporating a floor-standing cooler but with push-through fans and varying fin spacing, designed with the intention of reducing the dehumidifying effect caused by direct expansion (DX) refrigeration.
In addition to the cooler, the new equipment also included electronic expansion valves to modulate the flow of refrigerant and variable speed compressor and condenser fans to facilitate a more balanced and energy efficient system. In conjunction with their chosen design improvements JD Cooling were able to show the real potential of Performax™ LT as the new plant is showing a reduction in running costs of 25% compared to the previous equipment by delivering monthly savings in the region of 4,000 kW.
The installation consisted of 3 x Friga systems (Bitzer) FSMP6J-32ZY multiplexed semi-hermetic compressors in a packaged unit with 3 coolers, with a cooling capacity of 225KW, and evaporating temperature of -1°C to +1°C , condensing at 43°C. Total Cool elected to use Carel electronic expansion valves because they had settings for Performax™ LT and found them very user-friendly and easy to install. The flatbreads come out of the oven at a temperature of 80°C and need to be cooled very quickly to 20°C. This has been achieved and since the completion of the project both the customer and Total Cool have been pleased with the results of using Performax™ LT.
Cold Storage Plant for Fresh and Frozen Produce
Haulage Company Galtier chose Valentin Réfrigération to install a cold storage plant in Rodez in south-west France. Once again the system was intended to operate on R404A, but after consultation with Climalife France, the attraction of lower GWP and the prospect of a more energy efficient installation made Performax LT the refrigerant of choice.
Complementing the energy gain provided by Performax LT, performance is improved by the use of hot gas defrost and Kuba evaporators.
All these applications have shown that Performax LT can be successfully used instead of R404A in Dx systems. Although these examples are for new equipment, there is an equally valid case for converting existing R404A systems to Performax LT to achieve energy saving, use a lower GWP refrigerant and achieve carbon footprint reductions.