Ed Whinyates of Stonegrove Refrigeration highlights the importance of looking after refrigeration equipment and some of the options available.
We all know that if you buy a car and service it at regular intervals, then it performs to the standard that the manufacturer designed and reduces the risk of problems as the vehicle ages. All mechanical equipment needs periodic servicing to keep it in its best operating condition. Refrigeration is no different.
The ACR Journal talks to Hayley Nunn of Acorn Air Conditioning and Refrigeration, based in Bury St Edmunds.
Thomas Lergenmüller, Product Manager Screw Compressor Packages at GEA Grasso, looks at bringing down the all-important total cost of ownership.
Cost and competitive pressure on companies keeps growing in almost every industry where industrial refrigeration or air conditioning cooling is concerned. Efficient refrigeration systems are vital for economic, safe and sustainable production and storage in this area.
The focus of planners and investors aiming at modernisation or new construction of systems has long changed to encompass more than just low investment costs. The total cost of ownership (TCO) for the entire service life of a facility has become decisive instead.
The Institute of Refrigeration held a career development workshop for Women in RACHP to coincide with the International Women in Engineering Day.
The two-part networking session, hosted by training and consultancy specialists Cool Concerns in Tewkesbury, began with a practical event enabling non-technical staff to gain a hands-on understanding of refrigerant handling and brazing. This was followed by an interactive career development workshop with handy tips on career management and planning.
A shaky economic climate has led many people to adopt a 'make-do-and-mend' approach to HVAC plant rather than investing in new equipment. In fact, says John Grenville, Managing Director of ECEX, there is a useful halfway house – retrofitting – which offers an ideal opportunity to improve a building’s efficiency relatively inexpensively.
A system installed by Star Refrigeration in the year Margaret Thatcher became Prime Minister is still going strong after running 24/7 with no cooling loss for almost 40 years.
It was in 1979 that Star provided Associated Seafoods with two packages for their cold storage and production facilities on the Moray Firth coast in Scotland, making it the oldest plant in Star's history.
1 Don’t forget inhibitors
Glycol is an essential element of any heat transfer fluid used as part of a chilled water system, as it allows the fluid to be sufficiently chilled without freezing. However, an uninhibited glycol system can pose even more of a risk than plain water due to the highly corrosive nature of most glycols, so inhibitors must be used at all times.
For those operating in areas where there is a risk of incidental human contact, such as the food processing industry, the wrong inhibitors in an MPG solution creates a serious contamination risk, but an NSF-accredited glycol overcomes that.
2 Take regular water samples from various parts of the system
Corrosion and degradation can happen anywhere within a system and it’s not enough to take water samples from just one location. Samples need to be taken from available access points around the system and especially from high risk areas such as heat exchangers, cooling jackets and any other sensitive product-fluid interfaces.
3 Test fluid pH levels
Not taking pH level readings as part of routine water sampling can have a major negative impact on a system’s performance. While chiller pH tolerances will vary slightly depending on the materials used, I would recommend limits of 8.0 – 8.5. Incorrect pH levels may indicate that either not enough inhibitors have been used, or the glycol levels are too concentrated. Both scenarios can very quickly cause high levels of corrosion throughout a system if left unchecked, leading to costly maintenance bills and unplanned downtime.
4 Check the clarity of the sample
Not all tests are as in-depth as pH level, and one of the most obvious signs that a chiller system is degrading or corroding internally is when there’s visible debris in the water sample. A water sample from a chiller operating correctly should be clear and if it’s not, then there’s already some internal system damage. This needs to be addressed immediately as the debris can soon lead to blockages in key areas of operation such as the heat exchanger, which will rapidly decrease the chiller’s efficiency.
5 Chemically flush your system and chiller immediately after installation
As soon as a new chiller is installed, the whole system should be flushed immediately to ensure the fluid is completely free from contaminants and at the highest quality possible, with no legacy debris or surface contamination present to cause damage to the fluid, the pipework and the new equipment. This golden rule should be followed whether it’s a permanent or temporary installation for planned or reactive maintenance.
6 When in doubt, consult the experts
Given the intricacies of taking a thorough and correct chilled water system sample, sometimes it pays to call in an expert. Regular water sampling and off-site laboratory analysis is available as part of some chiller manufacturer’s aftersales and servicing packages – including Planned Preventative Maintenance Packages (PPM) from ICS Cool Energy.